DSEWebNet® is a global web based real-time control and monitoring solution for DSE control modules. It has been developed to support single and multi-set systems using a range of devices. The software includes mapping with static locations, real time instrumentation & control, event log tables and automatic system alerts. These can be sent to multiple users via email and SMS. The software can be viewed using laptop, desktop, tablet and smart phone devices.
SEWebNet® is an online service included with one of the following two devices.
DSE890 DSEWebNet® Gateway – 3G (GSM)/Ethernet
The Gateway connects to the DSE data server by integral Ethernet connection or GPRS (DSM or 3G mobile internet) and includes GPS (satellite location) functionality. This is most suited to remote and/or mobile locations.
DSE891 DSEWebNet® Gateway – Ethernet Only
The Gateway connects to the DSE data server by an integral Ethernet connection only. This is most suited for fixed installations where an ADSL / DSL cable broadband service is available (external broadband modem required, not supplied by DSE).
DSEWebNet® is also available as a smartphone or tablet app for Apple and Android devices.
|Minimises site visits.|
|Reduced maintenance costs.|
|Increased system up time.|
|ELECTRO-MAGNETIC COMPATIBILITY||ELECTRICAL SAFETY||TEMPERATURE|
|BS EN 61000-6-2
EMC Generic Immunity Standard for the Industrial Environment.
|BS EN 60950
Safety of Information Technology Equipment, including Electrical Business Equipment.
|BS EN 60068-2-1
Ab/Ae Cold Test -30°C.
|BS EN 61000-6-4
EMC Generic Emission Standard for the Industrial Environment.
|BS EN 60068-2-2
Bb/Be Dry Heat +70°C.
|BS EN 60068-2-6
Ten sweeps in each of three major axes.
5 Hz to 8 Hz @ +/-7.5 mm, 8 Hz to 500 Hz @ 2 gn.
|BS EN 60068-2-30
Db Damp Heat Cyclic 20/55° C @ 95% RH 48 Hours.
|BS EN 60068-2-78
Cab Damp Heat Static 40° C @ 93% RH 48 Hours.
|SHOCK||DEGREES OF PROTECTION PROVIDED BY ENCLOSURES|
|BS EN 60068-2-27
Three shocks in each of three major axes 15 gn in 11 ms.
|BS EN 60529
IP65 – Front of module when installed into the control panel with the optional sealing gasket.